When it comes to wood boiler efficiency, there is no end to the number of wood boilers advertised as being "high efficiency" boilers. How could practically all wood boilers be considered highly efficient? Is the term meaningless? Buyers, even those who are well informed, must find the landscape very confusing. One might think that a government website could help solve the confusion. However, even the EPA site listing approved wood boilers does not make clear which products will be the most efficient in actual use. What is going on?
Firewood, the Natural Fuel, is Difficult to Test
Wood and wood pellet boilers present unique challenges for establishing efficiency ratings primarily due to the unique nature of wood fuels. Firewood exists in various shapes, species, and moisture contents. Wood fuel also changes states as it burns; going from a drying phase, to a smoking phase, to a smoke ignition phase, to a charcoal burning phase. Each species of wood passes through these stages a little differently. Further, wood fuels do not ignite or extinguish quickly. Even wood pellets, which are highly processed, can have various moisture contents, pellet fragment size, and fuel value. For example, pellets made with softwood, counter-intuitively have more energy value than pellets made with hardwood due to the resinous pitch that is pressed into the pellet.
To help compensate for the variability of firewood and resulting impacts on wood boiler efficiency during testing, most US test methods limit allowable wood species. Due to wide geographic distribution, red or white oak test fuel is accepted throughout the US. As an interesting side note, to be compliant in Washington State, Douglas Fir must be used, as Washington State firewood markets are dominated by pine, spruce, and fir. Attempting to further reduce testing variability, until recently, all tests for firewood boilers required the wood to be cut into lumber with cross sections of 4" x 4".
The length of each 4" x 4" fuel stick is determined by a formula based on the depth of the firebox. After being cut to length, the wood is then nailed together with 3/4" spacers forming a test "crib". The crib of wood is basically a manufactured fuel pile nailed together with spacing in a neat, geometric pattern. Of course, that is not a realistic way to fire a wood boiler, so in addition to crib wood based testing, there are now at least two tests that allow for natural firewood to be used.
Multiple Test Methods Create Maximum Confusion
Regardless of attempts to improve wood boiler efficiency testing, human operation of wood fueled boilers is always a factor. For example, frequent on/off cycling of a boiler run when in shoulder seasons or a boiler filled with green wood or garbage can create terrible smoke and low efficiency. US regulators, responding to air pollution problems, have become increasingly interested in the performance of wood fueled boilers operating in such less than ideal scenarios. As a result, multiple test methods for wood fueled boilers now exist. This has had the unfortunate effect of allowing little comparability between boiler models tested with different methods.
There are two EPA approved test methods for testing wood pellet boilers. Additionally, there are three EPA approved methods for testing firewood boilers. One of those methods includes two annexes, effectively adding two other test methods. That makes a total of 5 firewood test methods. Further complicating the testing landscape, EPA also accepts European test results for some pellet boilers. As a counterpoint, much of Europe uses a single test method for firewood and wood pellet boilers, though increasingly, individual countries require small modifications to the standard.
EPA And "Hydronic Heaters" aka. Wood boilers
Driven by the EPA, in 2015 the US transitioned at the federal level from having zero mandatory testing for wood fueled boilers to an era in which all residential, wood fueled boilers must pass EPA testing to be legal for sale. Given the small pool of wood fueled residential boilers with any testing at all and given the high cost of testing, regulators accepted many existing results from the various test methods including the European test method. After 2020 the regulatory intent is that the number of available test methods will be reduced and boilers formerly tested to discontinued methods will require re-testing. While the primary goal of new tests is to reduce emissions from wood boilers, wood boiler efficiency is also a target value.
Why is European testing accepted by US EPA and other US regulators? Prior to 2015 and the advent of EPA certification, several states offered financial incentives for their citizens to install advanced wood fueled boilers. The incentives were in place due to renewable energy mandates and to help replace existing, dirtier and less efficient technology. A large percentage of advanced, wood fueled boilers eligible for incentives in 2015 were, and remain to this day, European. Due to the prevalence of European boilers, European test results were accepted prior EPA's involvement. New York State led the way by accepting European test results for their Renewable Heat New York program. Other states followed suit. European test data has been converted to US units of measurement in an attempt to provide units that correspond with typical US test data.
The ability to convert test data from customary European units of measure to customary US units of measure doesn't alone create a true comparison. The problem is that there is minimal harmonization between test methods. For instance, US tests require wood fueled boilers to be tested at four different burn rates, <15% of nominal output, <25% of nominal output, <50% of nominal output, and at 100% output. Results of each test are then averaged using weighting, with 2/3 of weighting placed on the two lowest output tests, which is when boilers are typically operating most poorly. The nominal output test receives only 5% weighting. The weighting scheme is an attempt to demonstrate boiler operation in a typical scenario.
By contrast, Europeans test wood fueled boilers at nominal output and at 30% of nominal output. Both results are published. Think city and highway MPG ratings for vehicles. There is no weighting or averaging of results. Europeans have stated that operating a boiler at 30% of nominal output is the typical limit of good performance. Using the theory that wood fueled boilers should not be operated outside the limits of good performance, Europeans have not required testing with very low boiler output.
The Impact of Fuel Moisture Content on Calculating Efficiency Results
Further complicating test results, when it comes to efficiency, European efficiency is reported using the lower heating value (LHV) of wood fuel whereas in the United States, efficiency is reported based on the higher heating value (HHV) of wood fuel. Here is a brief explanation of the difference between HHV and LHV and how heating values impact reported efficiency: When any fuel is burned, depending upon the moisture content and quantity of hydrogen in the fuel, there will be a release of water, typically in the form of steam, most of which is lost in the exhaust. The conversion of water to steam requires energy. For the HHV of fuel, the energy "held" in the steam is accounted for and added to the fuel value. If the exhaust can be condensed and the heat in the steam re-captured, then HHV makes perfect sense. Stated slightly differently, HHV is a measure of all available energy in the fuel assuming that heat in converted steam can be recaptured. Using the LHV of a fuel does not account for energy used/lost to produce steam. Consequently, if boiler efficiency is based on the amount of energy put into the boiler versus the amount of energy output, using the HHV of a fuel will result in a lower efficiency rating.
In practice, that means that boilers tested using the HHV of wood fuel, as we do in the United States, generally have substantially lower reported wood boiler efficiency than boilers tested in Europe purely as a result of how the efficiency rating is calculated. For example, a boiler tested in Europe with a 92% efficiency rating LHV will have an 82% efficiency HHV rating based on 25% moisture content fuel. As test fuel moisture content increases, the disparity between HHV efficiency and LHV efficiency increases. Those results will be very different even before the impacts of disparate burn rate categories mentioned above are added to the equation. Remember too, that these two efficiency ratings are for the same boiler and do not change how much heat is converted from wood fuel to heat in your house, or how many emissions will be produced in normal, everyday use.
Given all of these factors, when reviewing wood boiler efficiency it is important to recognize the following:
- If wood boiler efficiency is reported at 99%, it is almost certainly combustion efficiency.
- There are multiple test methods. US test methods will result in lower reported efficiency than European test methods.
- Using LHV or HHV for fuel will result in greatly different efficiency results. Europeans use LHV and the US uses HHV. A boiler tested with European methods will have higher efficiency results than the same boiler tested with US test methods.
- The US EPA list of certified hydronic heaters (https://www.epa.gov/compliance/list-epa-certified-hydronic-heaters) currently reports converted European test data alongside US test data. Efficiency ratings are therefore not easily comparable. Currently, the EPA list should only be used to determine if a boiler is certified or not.
- Wood boilers tested with actual firewood rather than crib wood will more authentically represent actual field use.
- Oil and gas boiler efficiency is somewhat comparable to EPA accepted wood fueled boiler efficiency ratings, but the comparison is far from perfect.
- Due to the more consistent nature of the wood pellet fuel and the near complete elimination of human operation, tested wood pellet boiler efficiency will more closely match actual field use than will test results for firewood or wood chip fueled boilers.
- Because existing US and European tests do not necessarily cause pellet boilers to cycle on and off during testing, efficiency may not match actual field use efficiency. Installations which limit on/off cycling and which allow a pellet boiler to have long run times will generally yield higher boiler efficiency.
- From a policy making standpoint, although firewood and wood chip boilers generally test less efficiently than wood pellet boilers, wood pellet fuels require at least 15% of their finished energy value to manufacture. That means that in many cases, considering the entire production cycle of the fuel beginning at the tree, firewood and wood chips are more efficiently converted to heat than wood pellets.
- Existing US tests for wood fueled boilers are somewhat accurate at predicting performance in the field, assuming the boilers are operated as required by the operator's manual.
- For firewood boilers, EPA restrictions on emissions are beginning to eliminate boilers that on/off cycle. The effect is that future boilers will have test results for efficiency that more closely match actual field performance.
It will be interesting to witness the ongoing evolution of wood fueled boiler testing. As this is being written there are rumblings of efforts in Canada to harmonize with European test methods. On the other hand, there are efforts in the US to develop additional tests which will be indicative of wood fueled boiler performance during on/off cycling. Some agencies in Europe are also discussing tests more like American tests. While it is helpful to have a single efficiency rating such as the AFUE rating found on oil and gas boilers, when it comes to wood fueled boilers, it seems that US consumers, policy makers, and regulators will face multiple efficiency ratings and ample confusion for several years to come.